Main >>Applications >> Sample problems >> Stress control tube
This is an example of the cable termination simulation, performed with QuickField software.
Axisymmetric problem of transient electric.
Relative permittivity of air ε = 1.
Relative permittivity of insulation ε = 2.
Relative permittivity of shield ε = 1.2.
Relative permittivity of stress control tube - nonlinear.
Voltage U = 4 kV.
Calculate the effect of electric stress reduction.
With stress control tube the maximal electric stress reduces from 1.6 to 0.5 kV/mm.